Leak Repair Maple Heights, Ohio
Over the years, aggressive water or constant use can cause your water pipes to develop leaks. VIP Plumbing Inc. has the experience necessary to quickly identify the source of your leak and repair it.
Whether your piping is copper, galvanized, plastic, or anything else, in Maple Heights, OH, VIP Plumbing Inc. is the one to call.
So. Industrial Ave MAPLE HEIGHTS, OH
Water meter going crazy
Marion St MAPLE HEIGHTS, OH
Tested gas house line starting at the meter. Found several leaks on the gas line and will write up an estimate with the cost of repairing these lines. Also repaired two water line leaks. On the estimate there will also be time to repair any other water line leaks. Dry wall repairs to be done by others.
Libby Road Down MAPLE HEIGHTS, OH
Tested double check back-flow preventer in a vault. Shut off valve passed. Check #1 - 1.4 Pass Check #2 - 1.7 Pass
Mid West Avenue MAPLE HEIGHTS, OH
Replaced 2 - 1/2 valves with new ball valves. Capped off and removed ice maker line.
E. 141st St. MAPLE HEIGHTS, OH