Water or Steam Boiler Repair Brecksville, Ohio
If your heating system in Brecksville, OH is not working it is likely your boiler needs repair or a good servicing. At times the fix is simple, at times not. Our heating service technicians have years of experience working on hot water or steam boiler systems like yours in Brecksville, OH. VIP Plumbing Inc. service vehicles are on call 24 hours per day are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our boiler repair, service or replacement pricing is competitive. Our estimates are always firm with no hidden surprises. You can rely on VIP Plumbing Inc. to advise you properly and to do excellent work promptly.
Re lit hot water boiler and repositioned thermal couple. No Warranty
Glen Valley Road BRECKSVILLE, OH
Went to check fill valve on steam boiler. Home owner said everything had been working fine for the last week or so from when he called. Home owner decided not to have us test anything and just pay a trip fee.
Glen Valley BRECKSVILLE, OH
Installed two new 3/4 zone valves. Erie pop tops. Added 3 new 3/4 ball valves to isolate the zone valves. Added a new 1/2 ball valve for the outside sill cock. Added anew 1/2 ball valve for the water feed to the boiler. Installed a new Central Brass top feed laundry tray faucet. Found that the zone valves were all installed flowing the wrong direction. Turned them the correct way. The thermostats that were wired to the zone valves were not properly installed. Extended the wire for the master bathroom thermostat and reconnected all the wires to the zone valves properly. The electrical power to the zone valves were also not wired properly. Corrected the 120 volt wiring as well as the wiring from the zone valves to the boiler controls. The system is now working properly with three sperate zones.
Highland Dr. BRECKSVILLE, OH